ULC is pleased to announce the publication of the Fifth Edition of CAN/ULC- S, Standard for. Inspection and Testing of Fire Alarm Systems. This National. Fire Alarm Inspection, Maintenance, and Service by Anubis Systems Technologies. SCOPE. This Standard provides requirements for the inspection and testing of fire alarm systems and specifies the devices and functions to be inspected.
||7 November 2006
|PDF File Size:
|ePub File Size:
||Free* [*Free Regsitration Required]
Pipe and fittings shall be inspected from floor level?
Gauges on dry system no low pressure alarm? Powered independently of the fire alarm control, these devices 5s36 normally not connected to it. Refer to Appendix F1 ; P iii Silent accelerated test. Check relief port on pressure reducer valves are not leaking? Ensure that the fire alarm system is fully functional?
Combination appliances individually inspected and tested. Hose properly racked or rolled? C F Checked for unusual noise or vibration? Seconds Are the results comparable to previous test?
P Emergency telephone operable or in-use tone at handset operates. Control valves opened until spring or torsion is felt in the rod? Individual alarm and supervisory input zone designation labels are properly identified. Where fault isolation modules are installed in data communication links serving field devices, wiring shorted cqn the isolated side, annunciation of the fault confirmed, and then a device on the source side operated, and activation confirmed at the control unit or transponder.
Test exhaust for excessive back pressure? We provide expert inspection services to all makes and models of fire alarm and extinguishment systems. If housing discolouration is noted, attempt to identify the source and note the date of manufacture.
Hydraulic name plate is properly affixed to the sprinkler riser? Defective intake screen for pumps taking suction from open sources? Batteries 2 voltage readings are normal Check accuracy of pressure gauges and sensors? Restricting orifice in place? H Confirm that the trouble transmission to the fire signal receiving centre is received. Output circuits for selective voice paging, including visual indication, F operates. Detector tubes must be pulled and their alignment confirmed if results indicate any abnormalities.
Trouble signal silence switch operates. Testing results and any exceptions are identified in the Device Test Record. Exceptions are identified in the Device Test Record. upc
CAN/ULC-S Fire Alarm Annual Inspection Test Form
Beam type smoke detectors inspected and tested. Recommended Additional Visual Inspection not mandated by the Standard: Failure to flush yard piping or surrounding public mains following new installation or repairs? The montly test is to ensure that all audible and visual alarm indicators function properly and are loud or visible enough to alert all the occupants to a fire condition. Yes No Pump run for ten 10 minutes Test log reviewed via visual display at controller?
In this instance the detectors are powered by a stand-by battery that will ensure continued protection even in the complete absence of electrical power or a “brown-out”.
Engine hour clock reading: The attached reports comply with Canadian Inspection Standards upon which they are based. Fire Alarm System Inspection Services.
Standards Council of Canada
A security or fire alarm system that employs integrated smoke detectors is by far the best way to protect your family or workers. Electrically Driven Pump Test Is the controller performing run tests automatically?
The fire signal receiving centre transmitter is located remotely from the fire alarm control B unit. Combination multi-criteria detectors inspected and tested? There are a number of companies in the Lower Mainland that perform this service.
Trouble signal on the voice communication system results in common trouble signal on the fire alarm system. Pressure reading at hydraulically most remote nozzle: A copy should be maintained on the premises for examination by the Fire Marshal or Inspector at their request.
Yes Ukc Last Service Date: Sensitivity tested results are recorded in the Device Test Record. Common audible trouble signal operates. Have someone standing by the panel so that they can cancel or silence any audible alarm quickly. Obstructive material discharged during water flow tests?